Architectures for integration of solar production
A photovoltaic system can be connected to the building electrical installation at different places: to the main low-voltage (LV) switchboard, to a secondary LV switchboard, or upstream of the main LV switchboard.
Recommended design: connect to the main LV switchboard
A recommended option is to connect the photovoltaic system to the main low-voltage switchboard of the electrical installation. If the conversion of the power produced by the solar panels is done by more than one photovoltaic inverter, it is recommended that the output of those inverters be grouped in a dedicated switchboard (PV switchboard), which is then connected to the main LV switchboard at a single point.
This architecture is simple and safe to maintain because the photovoltaic production can be disconnected at a single point. It is recommended for both new and existing buildings.
For existing buildings with small-scale PV production
Connecting PV generators to the closest secondary low-voltage switchboard is an architecture used mainly in existing buildings where the PV production is much lower than the building consumption. This approach is used primarily in existing multi-floor buildings, where the PV production, usually on the roof, is far from the main LV switchboard, which is usually at ground level. Indeed, in such situations, the cable length between the PV system and the main LV Switchboard can be considerable. Connecting the photovoltaic system to a secondary LV switchboard nearby can minimize cable length and facilitate the integration of the photovoltaic system.
However, this architecture presents important limitations, including:
- Complexity of the design, management, and maintenance of the installation, especially if there are several dispersed PV-sources
- Limited upgradability, because an increase in the PV system production capacity or the addition of other local production or storage may require significant changes such as resizing the existing electrical infrastructure
For existing buildings with PV production exceeding the demand
Connecting the PV system upstream of the main low-voltage switchboard is frequently the approach taken in existing buildings when the PV production being added is higher than the building’s consumption. In this case, connecting the PV system to a secondary or main switchboard would overload the existing electrical infrastructure and would require its modification, such as replacement of cables, switchboards, and protection equipment.
Making the connection upstream of the main switchboard provides a better option because it does not require any modification of the main LV switchboard or other downstream system components.