Installation, connection and sizing of cables with UPS
From Electrical Installation Guide
Warning! This page is currently being updated (as well as other pages in the same chapter), so you may encounter temporary inconsistencies in the content, or non-working links in navigation bar... We do our best to finalize these updates as fast as possible and minimize the impact for visitors. |
Contents |
Ready-to-use UPS units
The low power UPSs, for micro computer systems for example, are compact ready-to-use equipement. The internal wiring is built in the factory and adapted to the characteristics of the devices.
Not ready-to-use UPS units
For the other UPSs, the wire connections to the power supply system, to the battery and to the load are not included.
Wiring connections depend on the current level as indicated in Figure N28 below.
Fig. N28: Current to be taken into account for the selection of the wire connections
Calculation of currents I1, Iu
- The input current Iu from the power network is the load current
- The input current I1 of the charger/rectifier depends on:
- The capacity of the battery (C10) and the charging mode (Ib)
- The characteristics of the charger
- The efficiency of the inverter
- The current Ib is the current in the connection of the battery
These currents are given by the manufacturers.
Cable temperature rise and voltage drops
The cross section of cables depends on:
- Permissible temperature rise
- Permissible voltage drop
For a given load, each of these parameters results in a minimum permissible cross section. The larger of the two must be used.
When routing cables, care must be taken to maintain the required distances between control circuits and power circuits, to avoid any disturbances caused by HF currents.
Temperature rise
Permissible temperature rise in cables is limited by the withstand capacity of cable insulation.
Temperature rise in cables depends on:
- The type of core (Cu or Al)
- The installation method
- The number of touching cables
Standards stipulate, for each type of cable, the maximum permissible current.
Voltage drops
The maximum permissible voltage drops are:
- 3% for AC circuits (50 or 60 Hz)
- 1% for DC circuits
Selection tables
Figure N29 indicates the voltage drop in percent for a circuit made up of 100 meters of cable. To calculate the voltage drop in a circuit with a length L, multiply the value in the table by L/100.
- Sph: Cross section of conductors
- I_{n}: Rated current of protection devices on circuit
Three-phase circuit
If the voltage drop exceeds 3% (50-60 Hz), increase the cross section of conductors.
DC circuit
If the voltage drop exceeds 1%, increase the cross section of conductors.
a - Three-phase circuits (copper conductors)
50-60 Hz - 380 V / 400 V / 415 V three-phase, cosφ= 0.8, balanced system three-phase + N
In (A) | Sph (mN^{2}) | |||||||||||
---|---|---|---|---|---|---|---|---|---|---|---|---|
10 | 16 | 25 | 35 | 50 | 70 | 95 | 120 | 150 | 185 | 240 | 300 | |
10 | 0.9 | |||||||||||
15 | 1.2 | |||||||||||
20 | 1.6 | 1.1 | ||||||||||
25 | 2.0 | 1.3 | 0.9 | |||||||||
32 | 2.6 | 1.7 | 1.1 | |||||||||
40 | 3.3 | 2.1 | 1.4 | 1.0 | ||||||||
50 | 4.1 | 2.6 | 1.7 | 1.3 | 1.0 | |||||||
63 | 5.1 | 3.3 | 2.2 | 1.6 | 1.2 | 0.9 | ||||||
70 | 5.7 | 3.7 | 2.4 | 1.7 | 1.3 | 1.0 | 0.8 | |||||
80 | 6.5 | 4.2 | 2.7 | 2.1 | 1.5 | 1.2 | 0.9 | 0.7 | ||||
100 | 8.2 | 5.3 | 3.4 | 2.6 | 2.0 | 2.0 | 1.1 | 0.9 | 0.8 | |||
125 | 6.6 | 4.3 | 3.2 | 2.4 | 2.4 | 1.4 | 1.1 | 1.0 | 0.8 | |||
160 | 5.5 | 4.3 | 3.2 | 3.2 | 1.8 | 1.5 | 1.2 | 1.1 | 0.9 | |||
200 | 5.3 | 3.9 | 3.9 | 2.2 | 1.8 | 1.6 | 1.3 | 1.2 | 0.9 | |||
250 | 4.9 | 4.9 | 2.8 | 2.3 | 1.9 | 1.7 | 1.4 | 1.2 | ||||
320 | 3.5 | 2.9 | 2.5 | 2.1 | 1.9 | 1.5 | ||||||
400 | 4.4 | 3.6 | 3.1 | 2.7 | 2.3 | 1.9 | ||||||
500 | 4.5 | 3.9 | 3.4 | 2.9 | 2.4 | |||||||
600 | 4.9 | 4.2 | 3.6 | 3.0 | ||||||||
800 | 5.3 | 4.4 | 3.8 | |||||||||
1,000 | 6.5 | 4.7 |
For a three-phase 230 V circuit, multiply the result by e
For a single-phase 208/230 V circuit, multiply the result by 2
b - DC circuits (copper conductors)
In (A) | Sph (mN^{2}) | |||||||||||
---|---|---|---|---|---|---|---|---|---|---|---|---|
- | - | 25 | 35 | 50 | 70 | 95 | 120 | 150 | 185 | 240 | 300 | |
100 | 5.1 | 3.6 | 2.6 | 1.9 | 1.3 | 1.0 | 0.8 | 0.7 | 0.5 | 0.4 | ||
125 | 4.5 | 3.2 | 2.3 | 1.6 | 1.3 | 1.0 | 0.8 | 0.6 | 0.5 | |||
160 | 4.0 | 2.9 | 2.2 | 1.6 | 1.2 | 1.1 | 0.6 | 0.7 | ||||
200 | 3.6 | 2.7 | 2.2 | 1.6 | 1.3 | 1.0 | 0.8 | |||||
250 | 3.3 | 2.7 | 2.2 | 1.7 | 1.3 | 1.0 | ||||||
320 | 3.4 | 2.7 | 2.1 | 1.6 | 1.3 | |||||||
400 | 3.4 | 2.8 | 2.1 | 1.6 | ||||||||
500 | 3.4 | 2.6 | 2.1 | |||||||||
600 | 4.3 | 3.3 | 2.7 | |||||||||
800 | 4.2 | 3.4 | ||||||||||
1,000 | 5.3 | 4.2 | ||||||||||
1,250 | 5.3 |
Fig. N29: Voltage drop in percent for [a] three-phase circuits and [b] DC circuits
Special case for neutral conductors
In three-phase systems, the third-order harmonics (and their multiples) of single-phase loads add up in the neutral conductor (sum of the currents on the three phases).
For this reason, the following rule may be applied:
neutral cross section = 1.5 x phase cross section
Example
Consider a 70-meter 400 V three-phase circuit, with copper conductors and a rated current of 600 A.
Standard IEC 60364 indicates, depending on the installation method and the load, a minimum cross section.
We shall assume that the minimum cross section is 95 mm^{2}.
It is first necessary to check that the voltage drop does not exceed 3%.
The table for three-phase circuits on the previous page indicates, for a 600A current flowing in a 300 mm^{2} cable, a voltage drop of 3% for 100 meters of cable, i.e. for 70 meters:
Therefore less than 3%
A identical calculation can be run for a DC current of 1,000A.
In a ten-meter cable, the voltage drop for 100 meters of 240 mN^{2} cable is 5.3%, i.e. for ten meters
Therefore less than 3%